Trades Job Completed Note
Installed new switchboard with safety switches to replace old ceramic fuse board. Installed new earth electrode and main earthing conductor. Installed new LED down lights to replace old fluorescent light fittings.
Replaced damaged power point and mounting block at the entrance. Installed new interconnected hardwired smoke alarms. Arranged for Electrical Inspection. Supplied and submitted a Certificate of Electrical Safety.