Trades Job Completed Note
Signage contractor removed live photoelectric cell causing a short circuit. Circuit breaker was reset leaving unterminated live cables exposed close to metal exterior of building. Installed new photoelectric cell and extended cables to allow for new sign to be installed. Tested photoelectric cell for correct operation, All okay,
supplied and submitted a certificate of electrical safety.