Supply and installation of 1 x new under sink pump station sani pump
Before Starting the Job
After Job Completion
Trades Job Completed Note
Our finding: The existing sani pump's motor has overheated and burned out. Need a new replacement.
A new sani pump installed. Some pipework adjusted. The new pump line checked and tested to ensure all are working correctly.